Getting things set up on a new acreage! This install is per our county requirements.
You can see the Mad County Build install here: youtu.be/Qbf6r3CL8Fg
Thanks for watching! Subscribe, Like, + Share if you enjoyed this video!
Amazon Store | Project Tools Listed by Category
Finishes, Fixtures, Decor, + More
Mad County Build Series 100+ Videos
Thanks for stopping by our channel! We are self building our family of 5 a post frame barndominium in Iowa along with the life we’ve always dreamed of.
The goal of our channel is to inspire others to build their dream by providing education on construction and an in depth look at how we’ve gotten to this place.
PO Box 11
Winterset, IA 50273
#manufacturedhome #septic #install
On today's show we're going to talk about septic systems.
The model, my business is to build your dream and I'm super excited about this.
Because this septic system that I'm putting.
In is for my sister and brother-in-law on a piece of property.
They bought, this will be the future site of a post-frame building.
But while they save up some money, they decided to buy, a mobile home and move out and start establishing, their homeset I'm going to explain to you the ins and outs of a gravity-fed septic system and it'll be followed up by a full time lapse of the install.
So before you're able to do a septic system here.
You have to have a perk test a perk test is where they come out and do soil.
Borings to see what kind of soil you have and see if it will be suitable for a conventional.
We had that done, and they came back to the soil type.
And then they actually give you provide you a report with all the requirements of the septic systems that cost 400 to get that done here in this area.
And once you have that done you take that to the county, and you can pull a septic permit.
And then you have to abide by the perk test recommendations for the system, it's, a three bedroom.
So it requires a 1250 gallon.
Dual compartment septic tank.
It has to have 400 linear feet of field lines.
They have to be 26 to 36 inches deep, no more than 100 feet in length max.
So that means four lines 100 feet long.
There has to be a curtain drain, put on the top side of this system that basically keeps water out of your leach field.
But now that we got the bases done let's start.
This is the beginning right here where you connect to the house.
So we got four inch.
I use four inch schedule, 40 solid core pipe from the house.
Once you get it, you know, a couple feet outside the house you have to have a clean out that's code.
And then you have to have one every I believe it's, 75 or 100 feet.
I didn't have to worry about that because I'm only 30 feet to the tank.
We got our clean out.
And then from there, we go to the septic tank, which is right there.
And there is a quarter inch per foot drop from the house to the tank.
This is solid core pipe comes into the tank, the first compartment of the tank and then there's a t.
And what this t does is there's an eight inch drop, which is required here.
This t allows everything to go down into the liquid here in the tank, all the solids will settle to the bottom all the scum, and some of the paper will come to the top.
And then from there, the liquids will transfer over to the second compartment, which you can see the holes there they're about two thirds of the way up.
And then the liquids will come over here.
And the same process will happen.
So if anything happen to get over here, any solids they'll, settle at the bottom, any scum will come to the top.
And then here is your outlet, t, which has filter on it, which needs to be cleaned once a year just got to pull it out wash it off it's kind of gross, but it keeps your septic lines healthier.
So you can see the tea goes down so it'll pull.
It only allows liquid it won't.
Let the scum come off the top and go down this pipe, and it won't let solid.
So the liquids coming up into that pipe and then going out right here out of the tank.
We ran schedule, 40 solid core.
And after after the tank, you can get away with less drop.
Now I have plenty of drop here.
Just the way this land land lays its kind of slopes off, pretty good schedule, 40 solid core runs to the distribution box.
So this is a seven port distribution box.
Your inlet is going to be a little bit higher again.
You have to have a t.
So when that water or that liquid comes down, it can't just land in here and ripple the water.
It comes in here, hits that t goes down.
And then this water equally comes up, and you have these levelers on each line.
So you can distribute the water equally to all four lines.
I have these capped because they don't, obviously we don't need them.
So we have four lines going out they all have balancers on them.
So once we get water into this place, we'll put water in here and adjust these all so they're evenly distributing water to the lines.
Now my d-box is set on a bed of rock, and then I put rock up around it.
And then I will actually after inspection, which is here this morning I'll put some dry bags of concrete just around over these pipes.
And around this box, just to keep it nice and solid and secure.
So then from the distribution box, the liquid is going to go evenly into four lines.
Two of them go down that's, the farthest line that's the second to farthest line away.
And then these two come off and go to their own line.
So you just have to have a nice drop here, which I have more than enough drop to these lines.
And then once you get to the beginning of the line, this has to be supported.
So if there's any gap, I put rock under it.
So this comes right into this chamber system.
This chamber system is the infiltrator low pros, they're, 36 inches wide.
Um, these are 100 foot runs.
And then I always like to put a viewing port.
These are not required by code or anything like that.
The inspectors left she doesn't require.
They don't require these.
But I like to put them in, I just leave them stick up quite a ways until we get it all filled in it settles.
And then they get cut off.
And then the plug sits just flush with the ground.
So if you ever need to view in there or run a camera or for whatever reason I mainly put them in there for curiosity.
So you can see how much water's in there to see if they're even evenly getting water.
If they're holding water stuff like that, these are 100 foot runs.
My requirements were the bottom of the trench had to be 20.
I think it was either 24 or 26 to 36 inches deep.
As I ran these lines.
We used a laser level to make sure we were plus or minus an inch, the whole way down all right guys.
We got this curtain drain all dug out.
And basically what it is, there will be a perforated tile that runs the length of this ditch that I dug.
This is five foot deep.
I have a natural drop.
So I just kept it at five feet and the land just slopes off here.
So that works perfect.
It has to be ten feet above the last line, which it is.
And then once we hit this corner, this it's only required on the top side.
Once we hit this corner.
It just gradually comes up till it pops out down there.
So the water any ground water that comes through headed this way will hit this rock go to the bottom get in the tile and work its way out down there all right so to get started the first thing you have to have to have a conventional conventional septic system is slope.
You have to have enough drop that your septic lines coming from your house can drop quarter inch per foot to your septic tank.
Now, that's going to vary depending on where you're at in this country that's.
What is required here where we are located? So the first step for me was to come out here, shoot grade.
I use a transit, even though I could look at this and visually see that I would have enough slope all right so it's about 95 degrees and really humid out here.
Of course, we got our whole dog.
I got it close.
And then one, what I do is, I put some rock in the bottom and then just get it perfectly level.
So my tank is 64 inches wide.
And this is dug out where there's eight to 12 inches extra room on both sides and then it's 157 inches long.
And again, I have eight to 12 inches on each end of the tank.
So I have plenty of room to maneuver the tank.
However, I need to so I'm just adding a little rock.
I started my grade here, just using my transit level and I'm about right there.
I got to add a little rock back down in there and then we'll get this all tamped and check it again.
So just a a process that I like to do, I like to get it, absolutely perfect.
So when I set that tank in there and uh hit it with the the level, it's perfect, all right? So you can see I lined, I just roughly laid my pipe out.
I stuck a pipe into the tank, the inlet brought it out eyed up the 45 laid my pipe out in line laid out my fittings here.
And then what I did here since this isn't that far, um, you definitely don't want to over dig you want to be on undisturbed soil.
So I just broke the sod out and um, I have a pickaxe and a trench shovel.
So I'm gonna try to just I'm gonna go shoot my grade down.
There figure out how much drop.
I need so it's, 25 feet or it's 20.
I think it's, 20 feet I'll have to measure again, but I think it's 20 feet from there to here.
So I just got to figure out how much of drop.
I need it's, a quarter inch per foot drop.
So if that was the case I would need five inches of drop so I'll find out where I need to be there, and then make sure I'm five inches higher here.
And then we will get this all cleaned out.
So that pipe sits in there, nice, um on undisturbed soil, and then we'll start hooking we'll, get it all dry fitted.
And then we'll start hooking up from here and then work our way towards the tank since I can slide that pipe into the tank and bring it back carved rise from the lift into the sound.
They can hold us down, stand your ground.
We will stand cannot be undone by any one words breaking from the past raise up your fears tonight on the is you don't, oh all right guys.
I got this curtain drain all done.
All I got to do is put some, um, a barrier down between the rock and the dirt.
So the dirt over time, can't seep down into that rock and clog it up, even though I never think I don't think it would ever do that.
It would take a long long time.
I'm gonna go ahead and do that.
Anyway, we're gonna get the dirt pushed back in.
And then this is going to be complete.
The whole septic system will be complete it's been approved, we're, good to go.
If you guys have any questions, leave them in the comments.
I want to help those people who are wanting to kind of do some things on their own.
I believe that you should be able to.
And hopefully this video is helpful, too, if you're thinking about doing your own septic, like I said before, I'm located in southern iowa so make sure you check with your inspector and see what their requirements are, because every inspector is a little bit different.
I have found it very useful over the years to just give them a call if you're not familiar with working with them.
And just ask them, you know what they're looking for, you know what they want to see when they come for an inspection.
They want everything open do they by calling them you're, just you know, you're being professional and you're showing that you want to make sure it's done right so there's a lot of money just in materials that goes into a septic system.
So you don't want to screw it up and have to redo it.
So if you screw this up, they can actually make you move the location, the septic make sure you do it right? The first time.
And this is not something you want to do over the course of a month.
This needs to be done in a timely fashion in a week, get it done get the inspection get it covered up.
You don't want water on this if you don't have to, and if it gets enough water, they can also fail the inspection for that too and make you move it again.
We appreciate you guys watching, and we will catch you on the next video.
How to Connect to your Septic Tank. Typically, you will find a clean out is the easiest way to connect your RV to your septic tank. This will be a PVC pipe that comes out from the ground with a screw cap. You can simply remove the cap and attach the sewer hose from your RV into this clean out.How do you hook up a trailer to a septic tank? ›
How to Connect to your Septic Tank. Typically, you will find a clean out is the easiest way to connect your RV to your septic tank. This will be a PVC pipe that comes out from the ground with a screw cap. You can simply remove the cap and attach the sewer hose from your RV into this clean out.What is line from house to septic tank called? ›
Leach lines are a draining system. Leach lines start after the sewage water, also known as septic effluent, goes through the septic tank. In the septic tank, the sewage water gets treated by various enzymes and microbes. These enzymes and microbes begin breaking down solids.How deep is the septic tank outlet pipe? ›
Inlet & Outlet Pipes: Wastewater from your home enters the septic tank through the inlet pipe. After the solids settle out, effluent leaves the septic tank through the outlet pipe and flows to the drain field. The outlet pipe should be approximately 3 inches below the inlet pipe.How is a domestic septic tank set up? ›
- Installing a Domestic Septic Tank.
- Step 1 - Make sure you are prepared.
- Step 2 - Dig the hole.
- Step 3 - Install the base.
- Step 4 - Sit the tank.
- Step 5 - Backfill the hole.
- Step 6 - Install a septic drainage field.
- Step 7 - Connect the pipes.
What is this? While RV black holding tanks are utterly different from a residential septic system, septic-safe toilet paper will generally be safe for RV use. You'll want to verify with the packaging that it's genuinely septic safe, but also test to make sure it is.How big is a leach field for a 3 bedroom house? ›
If an absorption bed drainfield is used the minimum drainfield area shall be 100 square feet with an additional 50 square feet for each additional bedroom over two bedrooms.How often do you need to empty a septic tank? ›
Inspect and Pump Frequently
The average household septic system should be inspected at least every three years by a septic service professional. Household septic tanks are typically pumped every three to five years.
The distribution box receives effluent from the septic tank via one large pipe. Between four and nine lateral pipes run out of the distribution box and radiate outward in trenches to form the leach field.What size pipe runs from house to septic tank? ›
A watertight, 4-inch diameter Schedule 40 PVC pipe should connect the septic tank to the plumbing drains of the home. Slope the pipe 1/4 inch per foot (1/8 inch per foot minimum) toward the tank.
The inlet baffle should extend 12 inches above the liquid level of the tank. This is a total baffle length of 18 to 24 inches. The outlet baffle should extend 24 inches into the liquid depth and 12 inches above the liquid level, which is the elevation of the invert of the outlet pipe.What level should a septic tank be above the outlet? ›
A septic tank should always be “filled” to its normal liquid level, or the bottom of the outlet pipe which carries effluent to the absorption area. This normal liquid level is usually between 8” to 12” from the top of the tank on average (see picture at right).Does bath water go into septic tank? ›
Most, but not all, septic systems operate via gravity to the septic tank. Each time a toilet is flushed, water is turned on or you take a shower, the water and waste flows via gravity through the plumbing system in your house and ends up in the septic tank.What is the difference between a 2 chamber and 3 chamber septic tank? ›
Unlike the two-chamber design where the bottom of the tank is layered with gravel to separate the sludge from the water, the three-chamber design has a sealed bottom. Other than the sealed bottom, the three-chamber septic tank has two leaching chambers that dispose the wastewater from the septic tank.Do all septic tanks have a leach field? ›
Not all septic tanks have leach fields, but these are usually more expensive and not viable for many homes. Leach fields consist of an underground system of perforated pipes adjacent to your septic tank.Can you plug an RV into your house? ›
Is it Possible To Plug an RV Into a House Electrical System? While it's not recommended to plug RV into house power for extended trips, it is possible for a short amount of time. However, to do so, most RVs will require at least a 30/50 amp and a 15/20 amp electrical outlet.How close to septic tank does truck have to be? ›
Our trucks carry approximately 150 feet of hose on them, so we must be able to park within 150 feet of your tank. If your tank is further than 150 feet from a safe parking spot in your driveway or on the road, then you must let us know so that we can bring additional lengths of hose.